Not directly. If the CS15-L is connected to a CR200(X) datalogger, the datalogger can take the ac measurement and control a solid-state relay based on some threshold within the datalogger program. The solid-state relay can then control other relays, solenoids, or motor starters. (Use of a solid-state relay is preferred because the datalogger can trigger it with a small 5 Vdc mA signal.) For more information, see the “Measurement and Control Peripherals” section of the operator’s manual.